<oldText> Corridors shall be fire-resistance rated in accordance with Table 1020.1. The corridor walls required to be fire-resistance rated shall comply with Section 708 for fire partitions.

- Exceptions:
  1. A fire-resistance rating is not required for corridors in an occupancy in Group E where each room that is used for instruction has not less than one door opening directly to the exterior and rooms for assembly purposes have not less than one-half of the required means of egress doors opening directly to the exterior. Exterior doors specified in this exception are required to be at ground level.
  2. A fire-resistance rating is not required for corridors contained within a dwelling unit or sleeping unit in an occupancy in Groups I-1 and R.
  3. A fire-resistance rating is not required for corridors in open parking garages.
  4. A fire-resistance rating is not required for corridors in an occupancy in Group B that is a space requiring only a single means of egress complying with Section 1006.2.
  5. Corridors adjacent to the exterior walls of buildings shall be permitted to have unprotected openings on unrated exterior walls where unrated walls are permitted by Table 602 and unprotected openings are permitted by Table 705.8.

</oldText> <newText> Corridors shall be fire-resistance rated in accordance with Table 1020.1. The corridor walls required to be fire-resistance rated shall comply with Section 708 for fire partitions.
In addition, corridors in buildings of Types IIB, IIIB, and VB construction and assigned Risk Categories III and IV in Table 1604.5, other than Group I, shall have a fire resistance rating of not less than 1 hour where such buildings are any of the following:

1. Assigned a Seismic Design Category C or D in Table 1613.3.5(1).
2. Located in a flood hazard area established in accordance with Section 1612.3.
3. Located in a hurricane-prone regions.

- Exceptions:
  1. A fire-resistance rating is not required for corridors in an occupancy in Group E where each room that is used for instruction has not less than one door opening directly to the exterior and rooms for assembly purposes have not less than one-half of the required means of egress doors opening directly to the exterior. Exterior doors specified in this exception are required to be at ground level.
  2. A fire-resistance rating is not required for corridors contained within a dwelling unit or sleeping unit in an occupancy in Groups I-1 and R.
  3. A fire-resistance rating is not required for corridors in open parking garages.
  4. A fire-resistance rating is not required for corridors in an occupancy in Group B that is a space requiring only a single means of egress complying with Section 1006.2.
  5. Corridors adjacent to the exterior walls of buildings shall be permitted to have unprotected openings on unrated exterior walls where unrated walls are permitted by Table 602 and unprotected openings are permitted by Table 705.8.

</newText> <expected> Corridors Corridors shall be fire-resistance rated in accordance with Table 1020.1. The corridor corridor walls required to be fire-resistance rated shall comply with Section 708 for fire partitions fire partitions.

- Exceptions:
  1. A fire-resistance rating is not required for corridors in an occupancy in Group E where each room that is used for instruction has not less than one door opening directly to the exterior and rooms for assembly purposes have not less than one-half of the required means of egress doors opening directly to the exterior. Exterior doors specified in this exception are required to be at ground level.
  2. A fire-resistance rating is not required for corridors contained within a dwelling unit or sleeping unit in an occupancy in Groups I-1 and R.
  3. A fire-resistance rating is not required for corridors in open parking garages.
  4. A fire-resistance rating is not required for corridors in an occupancy in Group B that is a space requiring only a single means of egress complying with Section 1006.2.
  5. Corridors adjacent to the exterior walls of buildings shall be permitted to have unprotected openings on unrated exterior walls where unrated walls are permitted by Table 602 and unprotected openings are permitted by Table 705.8.

In addition, corridors in buildings of Types IIB, IIIB, and VB construction and assigned Risk Categories III and IV in Table 1604.5, other than Group I, shall have a fire resistance rating of not less than 1 hour where such buildings are any of the following:

1. Assigned a Seismic Design Category C or D in Table 1613.3.5(1).
2. Located in a flood hazard area established in accordance with Section 1612.3.
3. Located in a hurricane-prone regions.

- Exceptions:
  1. A fire-resistance rating is not required for corridors in an occupancy in Group E where each room that is used for instruction has not less than one door opening directly to the exterior and rooms for assembly purposes have not less than one-half of the required means of egress doors opening directly to the exterior. Exterior doors specified in this exception are required to be at ground level.
  2. A fire-resistance rating is not required for corridors contained within a dwelling unit or sleeping unit in an occupancy in Groups I-1 and R.
  3. A fire-resistance rating is not required for corridors in open parking garages.
  4. A fire-resistance rating is not required for corridors in an occupancy in Group B that is a space requiring only a single means of egress complying with Section 1006.2.
  5. Corridors adjacent to the exterior walls of buildings shall be permitted to have unprotected openings on unrated exterior walls where unrated walls are permitted by Table 602 and unprotected openings are permitted by Table 705.8.

</expected>